25KVA UL1640 PORTABLE TEMP POWER GFCI 480V-120V CART: 10 x 120v, 20a GFCI Duplex
25KVA UL1640 PORTABLE TEMP POWER GFCI 480V-120V CART. SCOPE OF DEGINE: All Bossltg Temp Power CRT systems are assembled per UL1640 Standards. UL requires a main on/off single switch control. This is performed by 60A-480v line power fused disconnect with 45a – 600v fuses protecting the primary of a 25kv – 480v, 1ph to 120/240v, 1ph encapsulated transformer – Rated for OUTDOOR USE. The secondary voltage is connected to a 125amp-120/240v 1ph, 3p/4w, Grounded Neutral load center with main breaker and 10 – 20a, 1ph circuit breakers. This load center is installed in a Nema 4 enclosure. Green ON/OFF indicator light to alert operators of power. 10 – 20a, 120v GFCI duplex, TYPE WR, receptacles are positioned – 5 outlets down each side of enclosure. This package in mounted to a metal cart frame that can be moved by hand over solid surfaces. Unit has forklift pockets and a center point lifting eyes. Total system is UL performance tested, electrical, static load and environmental weather test simulated. This Bossltg product will carry a NEMA 3R Environmental Rating. After testing, system is UL Labelled, palletized, metal strapped, then plastic wrapped for shipments.
SPECIFICATIONS: 25kva UL1640 PORTABLE TEMP POWER GFCI 480V-120V CART DESIGN
TYPE: 2″ Metal square tubing designed 2 wheel CART design with forklift pockets, center point lifting eye with 4/0 grounding lug.
PRIMARY LINE PROTECTION: 60a, 480v, 3ph fused disconnect switch, MAIN ON/OFF system. 45 amp -600v fuses. Nema 3R Enclosure.
480V PIN/SLEEVE RECEPTACLES: N/A
TRANSFORMER: 25kva, encapsulated, 480v 1ph to 120/240v 1ph.
SECONDARY LOAD CENTER: 125a, MAIN BREAKER, 120/240v, 1ph, 3p/4w with Grounded Neutral. 12 Circuits with 10 – 20a, 1p branch 120v breakers.
120 VOLT GFCI DUPLEX OUTLETS: 10 x 20a, 120v GFCI duplex receptacles, WR rated with IN-USE weather-proof covers.
SEAL TITE TUBING: 1-1/4″ plastic tubing to load side of Disconnect switch to line side of Transformer. 2″ plastic tubing from load side of transformer to line side of LOAD CENTER.
WIRING: All wire will be sized to 115% of amp load rating. THHN 90* wire type within system.
UL CERTIFICATION: Boss will assemble and text his product to UL1640 Portable Job-site Electrical Distribution Standards.
UL LISTED MARK: The UL Mark will be labelled to the 25KVA UL1640 PORTABLE TEMP POWER GFCI 480V-120V CART. This mark will have a serialized number so that OHSA can track this product through the UL Certification system.
FALSE-HOOD REPRESENTATION: Just because an electrical assembler uses all UL Certified Electrical Components does not represent a product to be UL Listed. The company that is assembling the product has to be UL Qualified by Underwriter’s Lab and confirmed with a UL File Listing. A UL Listed Printed Decal distributed by UL’s Authorized Printer that will show a recorded individual serialized tracking number with UL Assemblers Company name. This UL Label must be installed in open view of operator.
Bossltg is registered as UL Certified Temporary Job-site Electrical Distribution UL1640 Assembler. Confirmation can be validated by going to www.ul.com. Go to the UL File Directory, type in BOSSLTG, INC. All Bossltg filings will be displayed.